ADDRESSABLE FIRE PANEL
NON COMPLIANT PANEL
UTC are supplying their new ZP2 addressable fire panel into the industry without zone LED boards. These can be purchased as an optional extra.
This is not in compliance with SANS 10139.
The form of zone indication should comprise a separate light-omitting indicator for each zone of the system (e.g. a LED matrix or illuminated mimic diagram), such that the indicating equipment is capable of simultaneous display of fire signals on every zone. (SANS 10139:2012 - Edition 3.2 - 22.214.171.124 c))
Any system being installed with this panel (or any other panel) with no LED zone indicators will be recorded as non compliant by the FSIB.